|Title:||Energy management study of an educational institution|
|Subject:||College buildings -- Energy consumption -- China -- Hong Kong -- Management -- Case studies|
College buildings -- Energy conservation -- China -- Hong Kong -- Casestudies
Buildings -- Energy consumption -- China -- Hong Kong -- Management --Case studies
Buildings -- Energy conservation -- China -- Hong Kong -- Case studies
Hong Kong Polytechnic University -- Dissertations
Department of Civil and Structural Engineering
|Pages:||73,  leaves : ill. ; 30 cm|
|Abstract:||Energy management studies on an educational institution, an University located in Hung Hom, were carried out to audit the energy consumption of major building services (B.S.) systems and to identify potential areas for energy saving. Billing records and annual energy consumption of each system were analyzed. Energy Management Opportunities (EMOs) were then identified for further evaluation in terms of potential savings and capital investment required. The major EMOs, prioritised based on the payback period and ease of implementation, contributing to energy savings were identified as follows: - Delay starting and early shut off of chiller plants - Reset chilled water supply temperature - Addition of Central Control and Monitoring System - Modification of the chilled water system from constant flow to variable flow system at Phase 3B and 4A/IC - Addition of motion detectors to switch off/reset energy consuming equipment at general teaching rooms and small offices - Addition of occupancy sensors to lecture theatres - Removal of unnecessary lightings at public corridors - Replacement of conventional ballasts by electronic ballasts at public corridors - Replacement of prismatic type light fittings by open louvre type at Library Result shows that achievable annual energy cost saving is $4.3 million, which is equivalent to approximately 12% of the annual electricity cost ($36.2 million) of the educational institution for 1997, while retaining the existing standard and comfort conditions. Results of this research work will not only lead to monetary saving due to more efficient operation of the systems but also can provide useful guidance and reference for carrying out energy conservation schemes for other educational institutions.|
|Rights:||All rights reserved|
Files in This Item:
|b15041086.pdf||For All Users (off-campus access for PolyU Staff & Students only)||4.1 MB||Adobe PDF||View/Open|
As a bona fide Library user, I declare that:
- I will abide by the rules and legal ordinances governing copyright regarding the use of the Database.
- I will use the Database for the purpose of my research or private study only and not for circulation or further reproduction or any other purpose.
- I agree to indemnify and hold the University harmless from and against any loss, damage, cost, liability or expenses arising from copyright infringement or unauthorized usage.
By downloading any item(s) listed above, you acknowledge that you have read and understood the copyright undertaking as stated above, and agree to be bound by all of its terms.
Please use this identifier to cite or link to this item: