|Author:||Chow, Lap-yan Ryan|
|Title:||Lightning protection, earthing and bonging systems in buildings|
|Subject:||Hong Kong Polytechnic University -- Dissertations|
Interior lighting -- Safety measures.
Buildings -- Electric equipment -- Safety measures
|Department:||Department of Building Services Engineering|
|Pages:||ix, ,  leaves : ill. ; 31 cm.|
|Abstract:||The aim of this dissertation is to highlight the importance of electrical bonding protection in buildings. A detailed survey on earthing and bonding system, lightning protection system in different local buildings are conducted. By comparing with the relevant international standards and local regulations, the common problems and inadequacy from design and installation is identified and suggestion is given. "Early Streamer Emission" system (ESE) design becomes popular in Hong Kong. It provides a more simple, cost effective and flexible system design compare with the conventional lightning protection system design. However, the increased risk of side-flashing should be considered when applying such a system in Hong Kong. After reviewing the testing procedure on the earthing and bonding system, it is found that the procedure is usually less defined than the standard test requirement. A full set of testing is always replaced by simply visual inspection. The reliability and safety aspect of the system is much decreased. Also. the earth resistance and earth loop impendence test is missed in most of the commissioning stage. It is important to carry out proper testing and commissioning for lightning protection, earthing and bonding systems to ensure the system components are properly installed. Visual inspection together with testing and measurement is recommended to be included. All the testing record should be well maintained. When there is any damage in the lightning protection system and earthing and bonding system, no immediately danger effect will appeared. This is the main reason why the routine maintenance is usually not addressed on the both system. As a result, protection to property and occupants in the buildings is not ensured.|
|Rights:||All rights reserved|
Files in This Item:
|b23563266.pdf||For All Users (off-campus access for PolyU Staff & Students only)||4.97 MB||Adobe PDF||View/Open|
As a bona fide Library user, I declare that:
- I will abide by the rules and legal ordinances governing copyright regarding the use of the Database.
- I will use the Database for the purpose of my research or private study only and not for circulation or further reproduction or any other purpose.
- I agree to indemnify and hold the University harmless from and against any loss, damage, cost, liability or expenses arising from copyright infringement or unauthorized usage.
By downloading any item(s) listed above, you acknowledge that you have read and understood the copyright undertaking as stated above, and agree to be bound by all of its terms.
Please use this identifier to cite or link to this item: